4 Way Switch
4-Way Switch TIPS
- Complex switch requiring great skill to install
- Has five total screws on it vs. a standard single-pole switch with just three
- WATCH 3 & 4-way switch videos below for help
- 4-way switch must be between two 3-way switches
- CLICK HERE to Get Tim's FREE & FUNNY Newsletter!
DEAR TIM: I'm pulling my hair out wiring a 4-way switch. What's the secret to 4-way switch wiring?
Do you need a special 4-way electrical switch or a 4-way light switch? At this point, my new wife thinks she married a dunce.
If you can teach me how to wire a 4-way switch, I'll be eternally grateful. If you can't help, I will be forced to admit defeat and will call an electrician. Robert M., Ft. Collins, CO
DEAR ROBERT: Listen, don't beat yourself up too badly.
4-Way Switch - Tough But Not Impossible
There are many people who are flummoxed by the mysterious 4-way switch. I liken the 4-way switch, and its first cousin the 3-way switch, to the famous Wizard of Oz.
CLICK HERE to watch my video of how to install a 3-way switch. You need two 3-way switches to make a 4-way switch work.
CLICK HERE to read how to install a 3-way switch.
Once you slide the curtain back, you can see the Wizard is just a person pulling simple levers. The same is true for these switches.
When you take away the plaster and drywall, you'll see these switches are as simple as grade-school addition.
4 Way Switch Wiring Is Special
The first thing you need to know is that the 4-way switch is indeed a very special switch. It's got a total of FIVE screws on it! (See photo above.)
A normal simple single-pole switch that you have to turn on a bedroom, closet or front-porch light only has three screws on it.
The two screws are for the power wire and the third screw is for the ground or earth wire.
Watch the following video to see a simple single-pole switch.
You need to really understand how current flows and is interrupted by a simple single-pole switch before you start to tackle a 4-way switch!
Free & Fast BIDS
Single Pole Switch Video
This is what most of the switches in your home look like. You need to understand this before you graduate to a 3-way switch, much less a 4-way switch!
3 & 4-Way Switch Screws
A 3-way switch has one additional screw for a wire and a 4-way switch has four screws plus the green grounding screw.
Multiple On & Off Locations
You use 4-way switches in situations where you want to control a light or other fixture from more than two locations. For example, the second-floor hallway lights in my own home are controlled at four different locations. To accomplish this, you must have two 3-way switches and two 4-way switches.
Placement In Circuit Critical
The placement of the 4-way switch(s) in the circuit is extremely important. A 4-way switch must always be in between two 3-way switches. I know this sounds confusing, but let's see how it is done in the real world if you were to remove the drywall or plaster from your walls and ceilings.
4-Way Switch Video
Watch this video to see where you must place a 4-way switch.
How To Wire A 4-Way Switch
For sake of discussion, I will describe the simplest and most straightforward manner I know how to wire a circuit with a 4-way switch. We would start the job by nailing up three electrical boxes to the wall studs.
If you've not watched the video above, go do it now as the following text will make much more sense.
This circuit will have the mandatory 3-way switches and the single 4-way switch. Let's number the electrical boxes 1, 2 and 3 and make the assumption they would be in a line as if the switches were in a very long hallway.
Feed Line Cable Into a 3-Way Switch
The number 1 box would be at the one end of the hallway. You feed into this box the line cable. This is the cable that contains a white neutral wire, a black continuous-hot wire and the bare ground wire. This continuous-hot wire is controlled by a circuit breaker or fuse.
A second cable leaves the number 1 box and proceeds to the number 2 box in the middle of the hallway. This cable has four wires in it; white, black, red and bare copper.
A second cable that contains these same four wires leaves the number 2 box and goes to the number 3 box at the far end of the hallway.
A final cable leaves the number 3 box and goes to the light fixture we are trying to control. This final cable is like the first one we installed in the number 1 box; it has just a white, black and bare copper wire.
Connect White Wires
In all three boxes, you connect the white wires to each other with a wire nut. You do the same with the bare copper wires and create a tailpiece of bare copper that connects to the green grounding screw on each switch. In each box you are left with black and red wires. These connect to the terminal screws on the switches.
Don't Cross Travelers
Since you are just concerned with the 4-way switch, look at the actual switch. Hold it up as if it were in the switch box.
You'll see two of the screws are on the bottom and two are on the top. In my example, you take the black and red wire from one of the three-wire cables and attach them to the bottom screws. These black and red wires in the two three-wire cables are called travelers.
It doesn't matter which ones. Then you take the red and black wires from the other cable and attach them to the top screws of the 4-way switch. Once again, it doesn't matter which color wire goes on which screw. Assuming you did not take apart the 3-way switches in your circuit, your 4-way switch will now work perfectly.
Many Many 4-Way Switches
You can have many 4-way switches in a circuit. As crazy as this sounds, you could have 10 switches control one light. This circuit would have the mandatory two 3-way switches and eight 4-way switches.
Must Understand 3-Way Switches!
To make any of these circuits work correctly, you must connect the wires to the right screws on the 3-way switches. WATCH my 3-way switch video now.
Look closely at the 3-way switches. They'll have a black screw and two brass ones.
Connect the black continuous-hot wire in box number 1 and the black wire that goes up to the light fixture in box number 3 to the special black screw on each 3-way switch.
The remaining two wires at each box connect to the brass screws on the 3-way switch.